Antwerp, Chemical Storage Plant
After the existing fire extinguishing installation was refilled with new non Newtonian foam concentrate, the mechanical proportioner didn't function anymore. Refitting with a Foammaster Bladdertank Refit solved the problem. The existing equipment will be in safe operation for many years to come.
Water pressure about 10 - 12 Bar.
Water flow 5.000 - 16.000 ltr/min.
Proportioning rate 3% or 6%
Pressure drop about 1 Bar at maximum flow.